This homeowner in Carmel, IN called Indiana Home Comfort Solutions and expressed his concerns, explaining that his ductwork need fixed because some areas of his home were not getting cool. Being experts at providing ductwork solutions, Indiana Home Comfort Solutions inspected the home and ductwork.
Upon inspection, it was found that the ducts had 299 CFM of leakage, which is equivalent to a 57 square-inch hole. This amount of leakage was preventing cold air from reaching certain areas of the home, thus causing the temperature differences. Indiana Home Comfort Solutions sealed the ducts using Aeroseal Duct Sealing System and installed a return air vent in the basement to increase temperature balance and ensure proper air flow among the ducts. Based upon measured leakage reduction and original register flow, these solutions provided the homeowner Heating and Cooling capacity with a 16% improvement!